We have no complaints at all. Great service and follow up on our inspections every year.
Thanks so much Alex!
Had the team at my facility today during a fire alarm so they could monitor their newly installed alarms in our building as well as assist me in resetting the alarms after the drill. They told me alot and answered all of my questions. Great, great service.
To start with the wrong mag locks were installed creating screw holes in new doors that now have to be filled and painted. The new mag locks are now installed on the exit doors and seem to be ok but the wrong locks should have never been installed to begin with. The installer should have known you can not install that type of lock on an exit door in a nursing home.
Repaired maintenance switch.
I inspected the system for our permit.
Inspection for our permit.
INSPECTION ON THE SITE FOR OUR PERMIT.
FACP OFFICE: Check ground fault showing on simplex panel
Checked system signal strength and tested.
Annual Fire Extinguisher Inspection (70 FE's) Annual Kitchen Suppression System Inspection Pizza Hood - Ansul 101 20# Main - Ansul R-102 3G Annual Alarm Inspection
Completed Annual Smoke Alarm Inspection for 2018
Checked system due to communication fault.
Kitchen Suppression Repair
Integrity Fan Test for Acentek Colo #16. The Hold Time for this location is 23.1 minutes.
Completed Bi-annual inspection of all smoke detectors and heat detectors***All systems Normal and Reset ***