for Novi, MI
Heather - Novi, MI
Jenna - Novi, MI
Jeff - Novi, MI
Techs are awesome and very knowledgeable.
Response from Fire Pros, LLC:
We appreciate your feedback and 4 star review Jeff.
Good Service Techs
Jeff - Novi, MI
Getting a little slow on service. Seams like it takes a bit of time to get parts and return to complete the job.
Great service and very quick to respond with quotes.
John - Novi, MI
Jeffrey - Novi, MI
Sean is a pleasure to work with. He is very knowledgeable and willing to help you understand the system for trouble shooting problems that may occur with the sprinkler system.
Rob - Novi, MI
Bob - Novi, MI
Nice guys to work with
David Rozman - Novi, MI
I like fire pros. The guys that come in know what they are doing but always seem to have fun while doing their job. It is enjoyable to work with them.
Very Professional, Friendly, and Great Service
Lisa - Novi, MI
I think your company is lucky to have such a great employee!
Portable Extinguishers Installation
CHECKED CUSTOMER REPLACEMENT OF DIALER AND NAC PNL BATTERIES ALSO RE-LOAD TESTED FACP BATTERIES EVERYTHING PASSED WITHIN NORMAL LIMITS ***All Systems Normal and Reset ***
Industrial/Dry Chemical Suppression Inspection
1/31-Alberto Garcia de Alba confirmed the semi-annual kitchen suppression inspection/aware of alarms NWKitchen Suppression Inspection ***NEW CONTRACT BEGAN 08/2019**** Semi-Annual Kitchen Inspection (1) Ansul 12 gallon system, Q-12 R102 Hood (1) Ansul 6 gallon system, R-6 R102 Hood Deficiency for Ansul R102 18G: Regulators and expellant hoses out of hydro date.Improper expellant cartridge in system. Deficiency for Ansul R102 18G: Improper protection over 10b range and tilt skillet on back side of main hood. Inoperable Deficiency for Ansul R102 18G: Electric fuel source and non fuel source under front and back side of main hood does not shut down during system actuation.
Completed annual inspections for 2020
TD 1.14.20 Laura called because a strobe wasnt't working, asked to have the inspection done a month early.Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-S3 (3)360 links (4)Nozzles Ansul R102-S3 (3)360 links (5)Nozzles Ansul R102-S3 (3)360 links (5)Nozzles Deficiency for Ansul R-102 S-3G chase: All 3 Ansul systems are out of hydro date.
and a Fire Pros representative
will contact you within 24 hours.
Providing faster, smarter, and more efficient fire protectionLearn more here