for Dearborn, MI
Always great service.
RJ - Dearborn, MI
We have used alex with fir pros many times for commercial jobs and they always do amazing work. Due to conditions beyond their control, they were not able to help us on the most recent job we had requested, but Alex explained very well what has to happen and how we should go about correcting some things. 5 stars for sure, and we always recommend them.
Mohamad - Dearborn, MI
Great Customer Service!!!!!!
Roger - Dearborn, MI
Jared was great. Called as I requested. He explained everything as he went to each floor. He also went over the whole inspection when he was finished. Made sure the contact information was correct. A great job out of the way.
marc - Dearborn, MI
Mustapha - Dearborn, MI
Awesome crew, did the job well and in a timely matter.
Response from Fire Pros, LLC:
Thank you for leaving your review! We greatly appreciate your feedback and are glad that we provided you valuable service! At your convenience, please consider sharing your experience on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
Bill - Dearborn, MI
10/14 Amanda, Mgr called for service. No cooking at 8:00 AM She'll be on duty km Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection (3) Ansul R102-S3 (1)360 link (2)500 links (12)Nozzles
10/14 Confirmed with Virgil. He'll meet you on site. km 10/13 emailed Virgil Kitchen Suppression Inspection Semiannual Kitchen Suppression System Inspection ( 1 Ansul 6G ) Deficiency for R-102 6G behind hood: Automan has red button and two exposed expellant hoses.
10/5 Confirmed with Reni. He requested 6:15. Emailed confirmation km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection (3)ABC's (1)K Semiannual Kitchen Inspection Ansul R102-D6 (5)500 links (4)360 links (16)Nozzles Ansul R102-S3 (1)360 link (4)Nozzles Deficiency for Ansul R-102 D - 6G right: Both systems out of hydro date.
Annual Extinguisher Inspection FireSoft Due Date: 09/11/2019
9/3 Service requested by Sonja. New hours now, so they are not cooking at 11:00 AM. Sonja will be on site for you km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semiannual Kitchen Inspection Ansul R102-D6 (4)500 links (2)360 links (11)Nozzles Deficiency for R-102 6G: Exhaust fan above convection oven not working prior to test. Deficiency: 1- K-Class fire extinguisher out of hydro date.
8/20 Confirmed with manager Yasmine, she'll let manager Shareeka know of the appt. km Kitchen Suppression Inspection Semiannual Kitchen System Inspection
Annual Extinguisher Inspection Portable Extinguishers Inspection 8/20 Scheduled with Mario mh
and a Fire Pros representative
will contact you within 24 hours.
Providing faster, smarter, and more efficient fire protectionLearn more here