for Dearborn, MI
Always great service.
RJ - Dearborn, MI
We have used alex with fir pros many times for commercial jobs and they always do amazing work. Due to conditions beyond their control, they were not able to help us on the most recent job we had requested, but Alex explained very well what has to happen and how we should go about correcting some things. 5 stars for sure, and we always recommend them.
Mohamad - Dearborn, MI
Great Customer Service!!!!!!
Roger - Dearborn, MI
Jared was great. Called as I requested. He explained everything as he went to each floor. He also went over the whole inspection when he was finished. Made sure the contact information was correct. A great job out of the way.
marc - Dearborn, MI
Mustapha - Dearborn, MI
Awesome crew, did the job well and in a timely matter.
Response from Fire Pros, LLC:
Thank you for leaving your review! We greatly appreciate your feedback and are glad that we provided you valuable service! At your convenience, please consider sharing your experience on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
Bill - Dearborn, MI
2/26-Leila confirmed the semi-annual kitchen suppression inspection/aware of alarms NWKitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Inspection (1) Ansul R-102 6 Gallon System Annual Extinguisher Inspection Portables
Perform required 12 year hydrostatic test/replacement on the kitchen fire suppression system parts that are required to be. Other major parts of the kitchen fire suppression system will not be due for 12 year hydrostatic test/repalcement until 2029. All work done in accordance with NFPA 17A. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is may not work properly due to
Found NAC Pnl 1 in trouble to due Batteries failed. Replaced 2-12 volt batteries with customer supplied stock. ***All Systems Normal and Reset ***
TD 1.23.20 googled business, called and spoke to Sonja she approved the inspection @ 10a TD 1.15.20 VM full - no msg TD 1.7.20 VM full - no msgKitchen Suppression Inspection
Alarm Systems Inspection
Alarm Systems Service Call
Special Hazards Inspection
Alarm Systems Repair, install breaker lock
TD 1.14.20 Eddie called to schedule @ 8aKitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Deficiency: Electric (non fuel source) on pizza oven does not shut down during system actuation.
Alarm Systems Service Call Shenique - smoke detector upstairs hallway is beeping
Met w/RJ from Action Lock Smith to Tie in Existing Fire Alarm to Newly Replaced Fire Exit Door. Door Does not have Existing Fire alarm wiring going to it. Action Lock Smith will be in contact with Best Buy Facilities to figure out if they want door added onto fire Alarm system. They will contact us back when connections are ready to be made and Tested.
Completed annual Fire Extinguisher and emergency light inspection for 2019
Mounted Extinguisher in Van and Inspected
Alarm Systems Service Call
Portable Extinguishers Inspection
Completed annual Fire Extinguisher inspection for 2019
and a Fire Pros representative
will contact you within 24 hours.
Providing faster, smarter, and more efficient fire protectionLearn more here